Pre Slab Building Inspections in Melbourne
Gain peace of mind with New Home Inspections slab pre pour inspection services
Serious errors in floor slabs can have disastrous effects on your property, both short term and long term, and can often go unnoticed for years until they become extremely expensive and stressful to fix. The expert team at New Home Inspections will identify any issues with the construction of your slab before it is poured. We will inspect and report on issues surrounding:
- Undersized materials
- Incorrectly placed materials
- Missing pads, beams and footings
- Omissions or left out materials
- Poor building practices
- Lack of termite protection
- Damaged vapour barrier membrane
It is vital to the slabs integrity, safety and design that a pre slab building inspection be carried out prior to the pouring of concrete. We ensure everything has been set up in compliance with the approved engineers design and drawings, the Building Code of Australia and other relevant codes and standards.
Serving across Melbourne, including the Cranbourne, Truganina, Lynbrook and Pakenham areas, New Home Inspection provides the expert service you need. Contact us today on 9708 2500 for trusted advice on pre contract inspection, rebuild inspection and our other inspection services.
What to expect in a slab pre pour inspection report
Slab Pre Pour Stage Inspection Report – Single
This Inspection was carried out on a single storey home of approximately 275 sq metres or 30 squares.
Slab Pre Pour Stage Inspection Report – Double
This Inspection was carried out on a double storey home of approximately 300 sq metres or 32 squares, what we found during this inspection was quite alarming and just goes to show you never know just what we will find!
Common mistakes found during a pre pour inspection
The widened beam running down the length of this slab under the Laundry/Study wall has been wrongly installed in the second internal rib in from the right hand side, instead of the third one, and as a result is not bearing over the installed screw piles.
The additional N12 bars around the external rib have not been lapped at any of the corners correctly.